Clogged Pump in Oakland, NJ
It is very common for our plumbers to come into a job thinking there is one problem and having to pivot our thinking to solve the real issue. That is what happened to a homeowner in Oakland, NJ. We went to the house to troubleshoot a sewage ejector pump, but actually found out that the pump was burnt out due to too much toilet paper being flushed down the toilet. We installed a new pump, tested it, & everything worked.
Failing Valve in Hawthorne, NJ
We received a call from a customer in Hawthorne, NJ stating he had no hot water and couldn’t figure out why. Upon arriving on site, our skilled plumber determined there was a problem with the valve. Due to the city’s hard water, the valve failed. The water heaterwas completely drained and replaced. To prevent this from occurring, Hawthorne Mechanical Contractors recommends either installing a water softener or having us come out once a year to flush out your water heater to increase its’ lifespan.